1/MYSB | 1 l (pack of 12 bottles)
2/MYSB | 1 l (pack of 2 bottles)
Cleaning with boiler pump:
Add Mayline SB with a concentration 1% and turn on the pumps to obtain an optimal mixing, ensure that the flow temperature do not exceed 40° C. For an optimal cleaning, close all the valves and leave open only the furthest circuit and clean it in circulation for minimum 2 hours, then close it and proceed with the next one in the same manner. After cleaning every single circuit, open all valves and let it in circulation on the whole heating circuit for 1 hours.
Cleaning with external flushing pump:
use the same concentration and manner to clean with the external flushing pump, but use an application time of 2 and a half hours for every single circuit, and of 1 and a half hours for the whole heating circuit .
For very sludgy systems or systems with large water volumes extend the application time! After the cleaning process, empty the heating system and rinse well the system with the clean water. For protecting the cleaned system insert a correct water treatment for radiant heating systems such as Mayline SBA.